Hometown: Penfield, PA
Hobbies: Travel, Mountain Biking, Hiking
Interesting Fact About Me: I have 20 years of HVAC experience.
Best Advice to Customers: Be Comfortable!
The Service Tech, Robert, looked up our file and knew the part needed. He was on-site in about 30 minutes and quickly fixed the issue.
Great company and employees!
Any time we need to call Gary’s, they are quick to respond and always pleasant and knowledgeable.
Bob did a great job. He even was helpful in putting the padlock back on the cellar doors.
Robert Bush is an outstanding technician, His attention to detail and his work ethic is outstanding. I highly recommend these guys they go above and beyond for there customers.
A job well done.
Bob was very knowledgeable . Answered all my questions. Nice personally .
We have had our heating system for six years. I had maintenance and repairs done on our furnace. Bob was very polite, kind, thorough and efficient. I am very pleased with the overall experience.
Robert Bush was pleasant and efficient and remedied the problem even though it might have been past his normal work hours. I would say he was an excellent represenative of Gary's.
Planned service agreement on Amana modulating Gas Furnace. HVAC complete
Planned service agreement on high efficiency Lennox furnace. Found flame sensor with low signal. We will replace.
24v transformer was blown. Replaced the transformer. Furnace is now up and running. Complete Checked statics. It's adjusted all the way down. Needs a couple more runs and would be good. Red tagged unit because return air is pulling from burner supply air.
Cleaned and serviced thermopride propane high efficiency downflow trailer furnace.
Planned service agreement on high efficiency communicating furnace. Wired humidifier to be controlled by smart thermostat.
Bleed boiler system. Diagnose vibration. Order parts. Make estimate for new hot water tank
replace fireplace control. Customer also does not want to run his heat pump in the winter only wants to heat with natural gas
Upstairs air vent blocked. Auto vent on scoop is leaking, the fill valve was not on. Replaced 2nd floor bleeder with Auto air vent. Replaced scoop air vent, replaced expansion tank. Filled system and adjusted pressure. Cleaned system. Very dirty. 2" of rust and soot under burners. Cleaned flame sensor and ignitor. Checked and adjusted gas pressures. All loops are returning hot. Complete.
Replaced pressure relief valve on high efficiency bosch combi boiler.
Planned service agreement on EverRest high efficiency gas furnace.
Cleaned and adjusted oil boiler. Repaired leaking oil fitting
Replaced sensor in Mitsubishi heating and air conditioning system
Pland service agreement. Found unit going out in error code. Soft lock out. Resolved issue.
Planned service on lennox zoned modulating furnace